Removing a radiator isn't as difficult as it may first appear. Any individual radiator can be removed without you having to drain the whole heating system.
First make sure that you have the right tools to do the removal.
Before you start removing a radiator be aware that the water in radiators can be very dirty due to corrosion caused by rusting, and/or corrosion and build-up of black magnetite sludge caused by the electrolytic action between dissimilar metals.
Even if you are able to pull back any floor coverings such as carpets and rugs, it's still a good idea to lay a waterproof sheet below the radiator that is to be removed to prevent any spillage, and water damage to furnishings.
Once you have prepared the area around the radiator you can begin.
Before removing a radiator you must first shut off (close) both valves connected to the radiator - the handwheel valve and the lockshield valve.
Use one of the adjustable spanners to unscrew (one at a time) the cap-nut holding either the handwheel or lockshield valve to the adapter in end of the radaiator, and the other to prevent the tail-pipe or valve from twisting when unscrewing the cap-nut. Make sure that you have your bowl and jug ready to catch the water!
Separate the valve just slightly from the radiator's adapter and catch the emptying water in the bowl. To speed up the emptying of water open the radiator's bleed valve to allow air to enter the radiator.
When the radiator is pretty much empty of water unscrew the cap-nut connecting the remaining valve from the radiator making sure that you catch any water spillage.
Most of the wall hung radiators are made of steel which means that depending on the size they can be very heavy even when empty of water, so it's advisable to have someone assist you when removing a radiator from it's bracket.
With assistance lift the radiator off the wall brackets and pour out any remaining water.
If you are replacing the radiator with a similar sized one you may not have to reposition the wall brackets. You may however, have to if the radiator is a different make and type.
Lift and place the radiator onto it's brackets and then reconnect the handwheel and lockshield valve to the radiator's cap-nuts using the spanners to firmly tighten.
Reopen the lockshield valve by using the same number of turns that was used to close it. Lock-off the valve shank with the locking nut before screwing on the covering cap on the lockshield valve.
Open the handwheel valve by turning anti-clockwise and allow radiator to fill. Hold a rag under the radiator's bleed valve and then open with key to allow the air to escape. close the bleed valve when water starts to come out.
Click here to visit online store.
Hi, My name is Shannon and I'm one of home-heating-systems-and-solutions.com readers. I'd like to thank you for the excellent information I've found on home-heating-systems-and-solutions.com, it's one of my favorite readings on the net. Warmest Regards Shannon United States
Thanks for the advice for removing an air lock from an indirect system. Had to change an inlet on my cistern. First time I have tried any home plumbing. After draining the cold tank system air locked when I refilled the tank. Garden hose and mains pressure up the tap sorted my problems. Would not have known what to do without the advice on the site. Many thanks Sean United Kingdom.
An excellent site. I have found it very usefull. I am currently in the design phase of a new house and have be pondering which heat system to use. From your site I have been able to choose the right system. Ross New Zealand
I enjoyed your site. Pat United States
A must have for new parents
Essential Baby Sleep
By Dr Maud
We're so excited to announce the launch date of our first children book 'The Special and Talented Dog Show'.
You can pre-order now by clicking here.
To read more about our children's books, click here.